Shae has been with the Clean Water Center since July 2018. He delivers salt to homes and does basic maintenance on softeners. He enjoys meeting new and interesting people at each appointment. On his free time, Shae likes to hunt, hike, and snowboard.
This customer was having issues with low pressure in the house from his old treatment equipment plugging up. 7 years ago they installed a micronizer prior to their pressure tank to help remove iron and odor from their water. Unfortunately over time the pressure tank loaded up with sediment created by the micronizer and caused significant pressure drop in their home. After evaluating their system it was determined that it was best if we removed the micronizer and started from scratch with a treatment solution that would not have the same reoccuring issues in the future. We removed and replaced their pressure tank, and installed a new high efficiency water softener and iron filter. The customer now has great pressure in the house, great iron free and odor free water, and uses way less salt than his previous system.